GLUBET格鲁电竞_格鲁电竞官网_格鲁电竞娱乐平台 瓦斯发电机组厂家济柴环能燃气发电设备有限公司为你介绍瓦斯发电机组气缸套的安装步骤：1 将未装橡胶封水圈的气
Green Ring Power, a manufacturer of gas generator sets, will introduce you to the installation procedures of cylinder sleeves of gas generator sets:
1. Install the cylinder liner without rubber sealing ring into the gas generator body, press the cylinder tightly on the upper end face, and then measure the distance of the upper end face of the cylinder liner protruding from the top face of the body with a depth micrometer caliper. This distance should be 0.04 ~ 0.15 mm.
2. Check whether the distance between the upper end faces of the two cylinder liners sharing the same cylinder head protruding out of the top surface of the gas generator body is within 0.04mm, and match the cylinder liner when exceeding.
3. After installing the rubber sealing ring as required, install the cylinder liner into the gas generator set body. At the same time, measure the cylinder liner bore size along the crankshaft centerline and the direction perpendicular to the crankshaft centerline at the specified position. The specified inner diameter is 135 mm. Its roundness and the tolerance of parallelism between its generatrix and the bore axis are 0.015 mm. When overhauling the engine, check whether there are cavitation holes around the water interlayer wall of the cylinder block of the gas generator set. Small perforations can be repaired carefully and suffocated, but the mating surface cannot be damaged or deformed. At the same time to clean up the blocked water and oil channel
What is the pretreatment system of gas generator set?
Gas power generation pretreatment system mainly has dust removal. Dehydration. Steady pressure. Constant temperature and variable load etc. In order to ensure the safety in the process of gas power generation. Reliability and economy. Gas power generation pretreatment system needs to be designed and planned according to different project characteristics.
Gas belongs to inflammable and explosive dangerous gas. Gas power generation pretreatment system must have excellent safety protection function. (For details, please see: What are the basic requirements for gas for gas generating units? All designs shall be based on the corresponding national safety codes. At the same time, the gas pretreatment system is one of the auxiliary mechanical equipment in the gas power generation project. Its reliability and economy will directly affect the operation of the generator set and eventually affect the production time of the entire power plant. Good reliability will bring considerable economic benefits to the operation of gas power plants. At the same time, it will also improve the social benefits of gas power plants.